The Six Most Common Reasons Why Ozone Water Treatment Systems Fail
Ozone water treatment frameworks are utilized for an assortment of uses. Almost 1.6 billion gallons of city drinking water is treated with ozone. Practically totally filtered water has ozone added preceding the packaging step. Various products of the soil washing tasks, particularly for prepared to eat food sources, use ozone to protect the food from microbes and different microorganisms. It is significant that the ozone frameworks in these applications work dependably.
Realizing what kinds of things can turn out badly can help regions and industry settle on more intelligent choices in regards to the sort of ozone water treatment framework to purchase and why different components are significant. In this article we are alluding to metropolitan/mechanical scale ozone generators. We will cover the six most normal reasons why ozone frameworks fall flat, procedures for forestalling these issues and legitimate instrumentation that can give an early admonition of likely issues.
Ozone Water Treatment Systems
Ozone water treatment frameworks take oxygen or dry ozone water air and convert the oxygen present into ozone. This ozone is then blended in with water for the particular water treatment application, for example disifection. There are various elements that can make these frameworks fizzle. This article attempts to bunch them into six classes.
The regular disappointment instruments include:
Discharge of Water into the Generator
Helpless Feed Gas Quality
Under Sizing the System
Helpless Ozone Transfer Efficiency
Ozone Generator Cooling
Mistaken Materials of Construction
Reverse of Water into the Ozone Generator
Business scale ozone generator can’t endure water entering the generator without having extreme harm. The potential for reverse exists since the gas should move from the generator into the water, so there is a pathway for water to discharge into the generator. This is compounded in light of the fact that ozone can be infused, by means of a venturi, into water that is at a higher pressing factor than that within the ozone generator. In case there is an issue with the activity of the venturi or some adjustment of the downstream hydrodynamics, water can be constrained into the generator.
It is normal to see check valves used to forestall the reverse of water, however check valves are not a solid gadget for this reasons, particularly given the extreme harm that can result from discharge. Check valves in this application have a high likelihood of disappointment. Most top notch ozone water treatment frameworks utilize a multi hindrance way to deal with reverse anticipation utilizing a few inactive and dynamic gadgets to identify and counter the discharge of water.
A model may be really look at valves, fluid snares and differential pressing factor observing interlocked with a regularly shut solenoid valve. Observing differential pressing factor depends on the way that in typical activity the pressing factor in the generator should surpass the pressing factor at the mark of infusion, in any case the gas would not stream into the water. Setting off a solenoid valve to close disposes of the pathway for the water to arrive at the generator. Utilizing a regularly shut valve implies that even with a deficiency of force, the valve is shut and the generator secured.
Another procedure that is utilized is to put instruments in the gas line or fluid snares that can recognize fluid water. These gadgets can be utilized to trigger the closure of the solenoid valve and the generator.
Without such assurance it is inevitable until a situation emerges that makes the reverse happen and harm the ozone generator.
Helpless Feed Gas Quality
Ozone generators require a wellspring of oxygen to make ozone. Ozone is essentially three oxygen iotas associated together (O3). The air that we inhale contains about 21% oxygen, and is worked from two oxygen particles (O2). You can purchase unadulterated oxygen from mechanical and clinical gas providers. It is additionally conceivable to make oxygen utilizing a supposed oxygen concentrator. Little forms of these gadgets are utilized for home clinical purposes. They likewise produce a gas that is amazingly dry which is 90-95% oxygen